The C-Bus to BACnet gateway supports DIN-rail mounting. Select the mounting position with adequate space and heat dissipation and connect the interfaces. The 10/100Base-T(X) Ethernet port is equipped with RJ45 connector. For the C-Bus connectivity, there is an RS-485 terminal available. A 24V DC power source must power the gateway.
If the default C-Bus address 29 is not free, to avoid C-Bus collisions, connect the C-Bus later after you change the C-Bus address (see Configuration).
|Power||ON when the power is connected, and the gateway operates properly|
|Prog||ON when the system is in programming mode (e.g. installation of a new license key)|
|Tx||C-Bus link layer transmit|
|Rx||C-Bus link layer receive|
|Max. number of C-Bus controllers||29|
|Max number of C-Bus data points||2950|
|Default C-Bus address||29|
|Default IP address||192.168.1.222|
|Ethernet connection||10/100Base-T(X), RJ-45||Power supply||24 Vdc, 0.6 A|
|Temperature range||-10 .... +60 °C|
|Mounting dimensions (L x W x H)||212 x 90 x 60 mm (83.5 x 3.5 x 2.4 inch)|
Designed and Made in EU